Here are some screenshots on how to configure a turbine meter in a RealFlo.
Changing Number Of Meter Runs
Here is where you setup the number of meter runs for your SCADAPack
The changes will be reflected on the side bar.
Pulse Meter Register Assignment
Lets say for the sake of this demo we have physically wired up the turbine meter to Channel 2 (CI2) on the SCDAPack 357.
Therefore, we have setup the Telepace program as such with Modbus register address as 30013 for that channel.
Now to assign the Modbus Address 30013 to the RealFlo.
Double-click the Run3 (FT-3688) from the side menu.
Change the “Input Register” as 30013.
Remaining Of Turbine Meter Configurations
We have elected Run3 to be our turbine meter for this demo.
Double-click the Run3 (FT-3688) from the side menu to bring up the Run3 configuration screen.
This Run3 configuration will popup. The next few screenshot shows my typical turbine meter setup (to start off with), but I normally change it during commissioning as more information becomes available to me.
I hope this helped you.